- Manual Download
- Commissioning instructions / system wiring diagram
- Specification and material of alarm industry
加拿大28走势图-加拿大28稳赚计划-pc加拿大28在线预测网站Doing Zero calibration of controller again. Calibration method: open the control cabinet door, the upper left corner of the red dial switch to the corresponding channel, the blue is the function of choice, set aside to ON that is selected. Regulation of all appropriated OFF, the corresponding channel is allocated to ON, a blue dial the last one to ON ("ZERO"), press the mute button, the blue dial toggle the last one to OFF, and then press the mute button. Zero calibration complete. Red dial back to the factory settings.
加拿大28走势图-加拿大28稳赚计划-pc加拿大28在线预测网站Check detector wiring, or measure the voltage of the detector between "24V" "GND" is 24V. Or whether the current of the detector between the “I+”, and “GND” between is 4mA.
加拿大28走势图-加拿大28稳赚计划-pc加拿大28在线预测网站Detector output abnormal, the proposed detector. Suggested to check the detector.